The relay type NC20 provides protection of shunt capacitor banks and harmonic filter circuits. The capacitor banks may have the following configurations:
Single Wye grounded.
Single Wye ungrounded (with a resistor on the output of the neutral unbalance voltage transformer in order to develop the appropriate input current for the unbalance protection).
Double Wye ungrounded.
The capacitor banks may be: internally/externally fused or fuseless capacitor units. A suitable compensation method is provided to compensate the inherent unbalance neutral current
Protections 37, 49 and 50/51 (RMS) are based on RMS value measurement of the three phase currents (fundamental and harmonics up to the 11th)
STANDARD PROTECTIVE & CONTROL ELEMENTS
Under Voltage - 27
Under Current - 37
Negative sequence overcurrent transformer - 46LT
Phase overcurrent side H and side L - 50/51
Maximum Residual Overcurrent - 50N/51N
Overvoltage - 59
Breaker Failure - BF
CT Supervision - 74CT
Trip Circuit Supervision - 74TCS
SW PACK OPTIONAL CONFIGURATION
Thermal with Pt100 Probes - 26
One USB Type B local port for communication with ThyVisor setup software
PRO-N NC20 IEC 61850 Certificate
In recent years the harmonic producing part of total load has increased continuously because of the massive usage of power electronic in all the voltage levels. Thyristor convertors, frequency convertors, thyristor switches and static var compensator, such as thyristor controlled reactors (TCR) and thyristor switched capacitors (TSC), are commonly adopted in industrial applications and power utilities.
Filter capacitor banks consist of capacitor bank and series connected air core. Their task is to absorb the harmonic currents generated by loads and all above mentioned power electronic devices.
The aim of NC020 is to provide a reliable and cost effective solution for such an application granting capacitor bank safe operations.